Forestry Hose Type 2 600 LB Test
The forestry hose type 2 600 lb test assembly supplied under this specification shall be constructed with superior quality materials. shall be observed in production of the assembly, in order to ensure its quality and durability. Hose furnished under these specifications will have a potential service life manufacturer’s warranty of five years barring mistreatment that would render it unfit for service. Upon delivery, the hose shall be free from defects in workmanship and materials.
Jacket Construction: The jackets will be woven evenly and be free of defects, including knots, lumps, or unsightly disfigurations that could jeopardize the integrity of the hose assembly. The warp yarn shall consist of ring spun polyester yarn. The use of filament or entangled yarn is expressly forbidden due to the lack of inherent abrasion resistance. The filler yarns shall be constructed of high strength, low elongation, filament polyester to reduce weight and increase flexibility. The jacket construction shall be a 1-2 woven twill pattern with the 2 over-crossing on the exterior of the jacket.
Abrasion Impregnation: Hose assemblies are available with polymer impregnation that provide additional abrasion resistance. Standard color: yellow. Color shall be pure and even in each hose. Impregnated hose shall meet the requirements of USDA 5100-187 for abrasion resistance.
Lining: The lining shall be a single-ply extruded tube of synthetic polyurethane to resist zone. The polyurethane tube shall adhere to the jacket to prevent delamination. The finished product will meet and exceed all potable water Mil-H-24606B standards for the manufacturing of lightweight fire hose. The use of the polyurethane lined fire hose is designed to increase packing ability and applications where lightweight fire hose is desired.
Performance: The minimum burst test pressure, when tested in accordance to NFPA 1961, on Key Type 2 diameters shall be 900 PSI. Service test pressures stenciled on the hose shall be in accordance with current minimum requirements of NFPA 1962. A valid USA/ULC Underwriters listing shall be in force.
Couplings: Expansion ring threaded or quarter-turn quick connect couplings available. For other configurations, please Contact TEAM RAWHIDE.